zoom for more details
1.1 kV (A.C) & 1.5 kV (D.C ) to Earth2 cores AL / CU conductor, PVC insulated, galvanised steel strip / wire armoured cables as per IS 1554 Part - 1.Conductor : AL up to 10 Sq. mm conductor are solid Cl. 1 as per IS 8130. And above 10 Sq. mm conductor are stranded round or compact round or compact shape conductor Cl. 2 as per IS 8130In CU 4 & 6 Sq. mm conductor are solid Cl. 1 or stranded round Cl. 2 as per IS 8130. 10 Sq. mm conductor is stranded round or stranded compact conductor Cl. 2 as per IS 8130Above 10 Sq. mm conductor are stranded round or compact round or compacted shaped Cl. 2 as per IS 8130.Insulation : PVC Type - A, as per IS 5831. (Option : HR PVC Type - C, as per IS 5831)Core Color : Red, blackInner Sheath : PVC / PVC tape as per IS 1554 (P - 1)Armouring : Single armouring of G.I. Wire or G.I. Strip as per IS 3975Outer Sheath : PVC Type ST - 1 as per IS 5831 (Option : PVC Type ST - 2 as per IS 5831 / FR Type / FRLS Type)Cable Color : Black (Options : Any other color as per requirement)
Cable Design Parameters
While ordering, in addition to the part number the following details shall also be advised: Conductor Type (Aluminium or Copper) and class of conductor (Cl. 1 or 2). Insulation Type – PVC Type A / C. Sheath Type – PVC Type ST – 1 / FR / FRLS; PVC Type ST – 2 / FR /FRLS.