Help us, Help You through our Kabel Assist Calculator. Simply type in the details and we will recommend the most ideal wire for you to use.
Full Load Current
Star Delta Starter
Direct Online Starter
We recommend 6 Core cable between Star Delta starter and Motor. If 6 Core cable is not available, use 2 Nos. of 3 Core unarmoured cable.
Nominal area of conductor
1.1kV-3, 3.5, 4Core RR kabel XLPE Cables
1.1kV-3, 3.5, 4Core RR Kabel PVC Cables
3.3kV, 6.6kV, 11kV-3 Core RR Kabel PVC Cables
Single Core RR Kabel XLPE Cables 3.8/6.6kV(E), 6.6/6.6kV(UE), 6.35/11kV(E)
3 Core RR Kabel XLPE Cables1.9/3.3kV(E), 3.3/3.3kV(UE), 3.8/6.6kV(E), 6.35/11kV(E)-35 to 400 sq.mm, 11/11kV(UE) -70 to 400 sq.mm, 12.7/22kV (E), 19/33kV(E)-95 to 400 sq. mmand 33/33kV(UE)-120 to 400 sq.mm
Current ratings for Building wires & Flexibles, in Amps. with Copper cond.
Current Rating for Power Cables with Aluminium conductors
- Figures in Red are Current Rating for Cables laid in Air
- Figure in Black are Current Rating for Cables laid in Ground
For Approx, current rating for Power cables with copperconductor increase the above rating by 25%
The above rating are normal rating & will subject to de rating factors for various conditions as per IS:3961